N-P: AF466A   -   NUEVA!!  HP UPS R/T3000 Low voltage - UPS - AC 100/110/120/127 V - 2.7 kW - 2880 VA - Unit Dimensions (HxWxD) 3.5 x 17.5 x 25 inches / 8.9 x 44.5 x 63.5 cm  Shipping Dimensions 11.25 x 23.48 x 36.25 inches / 28.57 x 59.64 x 92.07 cm  Unit Weight 82 lbs/37 kg  Shipping Weight 89 lbs UPS and 127 lbs ERM / 40.37 kg & 57.6 kg  BTU Break Down BTU On Line 540 BT/hr  BTU On Battery 1138 BTU/hr  Battery Type 12 V, 5 AH, sealed, maintenance-free, rechargeable, valve regulated lead-acid batteries with a 3-5 year service life at 25C (77F).  Electrical Input Voltage Range See Model Matrix for nominal and user selectable voltage settings  Frequency 50/60 Hz  Online Efficiency 95%  REPO Remote Emergency Power-Off disables AC power to load  Online Regulation -10% to +6% of nominal voltage  Electrical Output On battery Regulation ñ5% of nominal voltage  Voltage Wave Form Sine wave  Connections See Model Selection Matrix; divided into 2 Load Segments  Output Protection Re-settable circuit protectors  Type Maintenance-free, sealed, valve-regulated lead acid (VRLA)  Battery Extended Batteries Up to two ERMs supported  Backup Time See Backup Times Chart  Recharge Time <3 hours to 80% usable capacity; <48 hours for complete recharge  Serial Ports Standard DB-9 and USB ports (ships with communication cables)  Communications Option Slot One  Option Cards HP UPS Network Module  LED Indicators LED and switch membrane integrated into the front panel  Software HP Power Protector software available  Environmental and Safety Operating Temperature 10øC to 40øC (50øF to 104øF); UL-tested at 25øC (77øF)  Non-operating Temperature -20øC to 50øC (-4øF to 122øF)  Operating Humidity 20% to 80% (non-condensing)  Storage Humidity 5% to 95%  Operating Altitude Up to 6,562 ft (2000 m) above sea level  Transit Altitude 49,212 ft (15,000 m) above sea level  Audible Noise <45db in normal operation. <50bd on battery operation  Safety Markings NA/JPN: UL, cUL Int'l: GS, CE, GOST  Safety Certifications UL1778, UL60950-1; CSA22.2 No.107.3-05,; EN60950-1 IEC62040-1-1  REPO Port Meets NEC code 645-10 and 645-11and UL requirements   - UPS ONE LINE 5 CONECTORES RACKEABLE SOPORTA CON FUENTES DE 600W (20%)  HASTA 40 MIN Y CON FUENTES DE 1500W (20%) HASTA 5 MINUTOS  Garantia :Depende Configuraci¢n                                                               Para Precio por Volumen y Disponibilidad Llamenos en Bogota a los Telefonos : (571) 317 9422 - 23, o Envienos un Email a : Ventas@netcomp.com.co