N-P: AF461A   -   R5000 5000VA Rack-mountable UPS Hight voltage  Line-interactive UPS 4500W 200 - 208V  Technical Specification Unit Dimensions (HxWxD) 5 5 in (12.7 cm) x 17.2 in (43.7 cm) x 29.3 in (74.4 cm)  Shipping Dimensions (HxWxD) 14.4 in ( 36.58 cm) x 23.6 in ( 60 cm) x 38.78 in ( 98.5 cm)  Unit Weight 126 lbs (57kg)  Shipping Weight 192 lbs ( 87 kg)  BTU Break Down BTU On Line 478 all models  BTU On Battery 846 INTL, 1041 NA/JPN  Battery String Voltage 216V  Battery Type 12V 27W  Battery Quantity 18  Electrical Input Voltage Range 160-253V at 200/208V nominal; 176-253V at 220, 230, and 240V nominal  Frequency 50/60 Hz  Input Plug Part number AF460A: L6-30P, 3m cord Part number AF461A: IEC-309 32Amp, 3m cord  Online Efficiency 94%  REPO Remote Emergency Power-Off disables AC power to load  Electrical Output Online Regulation -10% to +6% of nominal voltage  On battery Regulation ñ5% of nominal voltage  Voltage Wave Form Sine wave  Connections See Model Selection Matrix; divided into 2 Load Segments  Output Protection Re-settable circuit protectors  Battery Type Maintenance-free, sealed, valve-regulated lead acid (VRLA)  Extended Batteries Up to four ERMs supported  Backup Time See Backup Times Chart  Recharge Time <3 hours to 80% usable capacity; <48 hours for complete recharge  Battery String Voltage 216V  Battery Type 12V 27W  Battery Quantity 18  Communications LED Indicators LCD and switch membrane integrated into the front panel; with five-button control (four buttons for UPS power control and one button under the front bezel for configuration).  Environmental and Safety Operating Temperature 50ø to 104ø F (10ø to 40ø C )  Transit Temperature -13ø to 131ø F (-25ø to 55ø C)  Storage Temperature 32ø to 77ø F (0ø to 25ø C )  Operating Humidity 20% to 80% (non-condensing)  Storage Humidity 5% to 95%  Operating Altitude Up to 6,60 ft (2000 m) above sea level  Transit Altitude 49,000 ft (15,000 m) above sea level  Audible Noise <45db (in normal operation)  Safety Markings NA/JPN: UL, cUL Int'l: GS, CE, GOST  Safety Certifications UL1778, UL60950-1; CSA22.2 No.107.3, No.60-1950; EN50091-1-1; EN60950-1 IEC62040-1-1  EMC Markings NA/JPN: FCC, VCCI, ICES, CISPR Int'l: BSMI, C-Tick, CISPR  Emissions FCC CFR 47, Part 15 Class A, EN50091-2  Immunity IEC 801-2, IEC 801-3, IEC 801-4, IEC 801-5  REPO Port Meets NEC code 645-11 intent and UL requirements   - Load (Percent*) With Internal batteries With One Extended Runtime Module (Minutes) With Four Extended Runtime Modules (Minutes)  25 44 143 436  50 16 44 145  80 7 25 83  100 5.7 20 64    Garantia :Depende Configuraci¢n                                                               Para Precio por Volumen y Disponibilidad Llamenos en Bogota a los Telefonos : (571) 317 9422 - 23, o Envienos un Email a : Ventas@netcomp.com.co